“My original condenser fan motor has three wires and the replacement condenser fan motor that I bought has four wires – did I buy the wrong motor?”
This is by far the most common post-transaction question that we receive from customers that have recently purchased replacement condenser fan motors. Simply put, no – you did not buy the wrong condenser fan motor. While most original condenser fan motors only have three wires, it’s very common for replacement condenser fan motors to have four. This guide will explain how to wire your new condenser fan motor using a four wire setup or a three wire setup when using a single run capacitor or a dual run capacitor.
A review of the components
If you recall from our residential cooling season guide, outdoor condenser units use a switch called a contactor. This switch is controlled by the thermostat and closes to complete an electrical circuit when electricity needs to be supplied to your condenser fan motor and compressor. Think of the contactor almost as a gatekeeper – electricity needs to be both supplied and returned through it in order for your system to function properly.
Condenser units also use a component called a run capacitor. Run capacitors allow condenser fan motors and compressors to run more efficiently and they’re rated by a unit of measurement called microfarad. Dual run capacitors are used for both your condenser fan motor and your compressor. Single run capacitors are used exclusively for just your condenser fan motor or just your compressor. Like your contactor, your capacitor needs to be wired correctly in order for it to function properly.
Using a dual run capacitor.
If you’re using a dual run capacitor, you’re only going to use three of the four leads coming off the new condenser fan motor.
You’re going to wire the black lead to where the black lead on your previous condenser fan motor was wired to. This will likely be back to your contactor. You’re going to wire the white lead to where the white lead on your previous condenser fan motor was wired to. This will likely be the “C” or “Common” terminal on your dual run capacitor. Finally, you’re going to wire the brown lead to where your previous brown lead was wired to. This will likely be the “F” or “Fan” terminal on your dual run capacitor. The brown lead with the white tracer will not be used for this setup. You can use a wire nut and electrical tape to tie it off.
NOTE: You'll need a jumper between the "C" or "Common" terminal on the capacitor and the return side of the contactor.
Using a single run capacitor with a four wire setup.
If you purchased a new condenser fan motor with a new single run capacitor, this will be the wiring setup that you’ll be using. You’re going to wire the black lead to where the black lead on your previous condenser fan motor was wired to. This will likely be back to your contactor on the supply side. You’re going to wire the white lead back to the return side of your contactor. You’re going to wire the brown lead to one set of terminals on your new capacitor and you’re going to wire the brown lead with the white tracer to the other set of terminals.
Using a single run capacitor with a three wire setup.
If you purchased a new single run capacitor and the condenser fan motor that you’re using only has three leads coming off of it, this will be the wiring setup that you’ll be using. You’re going to wire the black lead back to where it was previously wired. This will likely be back to your contactor on the supply side. You’re going to wire the white lead to one set of terminals on your new capacitor. You’re going to need to wire a jumper from this set of terminals back to the return side on your contactor. Finally, you’re going to wire the brown lead to the opposite set of terminals on your new run capacitor than the common lead.
Sum it all up.
There’s always a sense of fulfillment when completing a project yourself, but wiring a new condenser fan motor and run capacitor can be a bit tricky if you haven’t done it before. Safety is always the highest priority. Make sure the electrical supply to the condenser unit is disconnected before beginning any work. Use your multimeter to confirm the disconnection. If you’re not comfortable working with electricity, contact a local HVAC contractor and they will be more than happy to complete this task for you.
It’s very helpful to document the location of existing wire connections before removing the condenser fan motor or run capacitor. Use a camera to take pictures of the connections and reference the pictures when installing the new condenser fan motor and run capacitor.
Finally, this guide is intended to be used as a general overview of common condenser unit wiring schematics. Some condenser fan motors wire to a circuit board while others use proprietary plugs for their connectors. We strongly recommend referring back to your unit's manual for proper wiring instructions.
When replacing a condenser fan motor, it’s always advised to replace the condenser fan blade along with it. Here’s the reason why – condenser fan motors commonly fail when their bearings fail. The motor’s bearings often fail when the fan blade the motor is driving isn’t balanced properly. By replacing the condenser fan blade when [...]
The thermometer reached 75 this past weekend in Chicago, which means we’re officially entering cooling season. Cooling season is the industry term for when we use our air conditioning units – compared to heating season for when we use our furnaces. Most people cross their fingers when turning on their air conditioners for the first of [...]
The 5KCP39 line of HVAC motors is probably one of the most common in use today. We've seen hundreds, likely thousands, of condenser fan motors and direct drive furnace blower motors that have model numbers starting with the 6-digit sequence of 5KCP39.Before we begin - it's important to note that GE no longer makes fractional [...]
It's time to replace an old fan motor. You take the motor out of its housing, gather all the nameplate information, and you start looking at replacement options. You notice the listed motor rotations and think to yourself, what does CWSE mean? What does CCWLE mean? Well, have no fear! EMOTORSTORE put together a quick [...]
Welcome! After a thorough analysis of our e-commerce needs and how we can provide a better user experience to our customers, we decided to replatform our e-commerce site to Bigcommerce.The original EMOTORSTORE was launched in 1999 and quickly became one of the most respected electric motor e-commerce sites on the internet. The original site was replatformed [...]